Author
balakalees
View
232
Download
1
Embed Size (px)
7/28/2019 Convection Hmt
1/47
Q. 4.1. Define convection. Differentiate between free and forced convection.
Ans. Convection is the phenomena of heat transfer by actual bodily movement of particles of themedium. Convection is linked to heat transfer by transportation of medium itself and heat
transfer takes place due to intermixing of the particles. Free convection takes place due to
temperature changes which changes the density of the fluid. The hot fluid becomes lighter andmoves up whereas cold fluid moves down to take its place and so convectional currents are setup and energy transfer takes place by intermixing of the particles.
In forced convection, the flow of fluid (convectional currents) are caused by pump, fan, or
atmospheric winds. Heat transfer in forced convection is more than in free convection.
Q. 4.2. Write Newton  Rickman law/Or state Newtons law of cooling?
Ans. Newtons law of cooling states that
Q. convective heat flow rateh = co efficient of convective of heat transfer
A , surface area exposed to heat transfer
= surface temperature of the solid
= undisturbed of the fluid.
Q. 4.3. Define thermal boundary lay.
Ans. When hot fluid flows over the place exists a region near the plate where temperature
gradient exists. The region r tie plate where temperature gradient exists is called thermal
boundary layer.
Thermal Boundary layer thickness (6k) is defined as the value of transverse
distance y from the plate surface at which
7/28/2019 Convection Hmt
2/47
Q. 4.4. What is a Nusselt number? Explain its significance.
Ans. Consider the flow of fluid past the hot plate
At plate surface0 the energy transport can occur only by conduction.
From energy balance, heat conducted through the plate must be equal to heat transfer by
convection into rest of the fluid.
The dimensionless number hl/A is called Nusselt number
Nusselt number is the ratio of temperature gradient at the surface to the overall
reference temperature gradient.
7/28/2019 Convection Hmt
3/47
Q. 4.5. Define:
(i) Reynold No. (ii) Grashof No. (iii) Prandtl No. (iv) Stanton number.
Ans. (i) Reynold No. : It is the ratio of inertia forces to viscous forces
ReNo.= Inertia force = = pVlViscous force
(ii) Grashof Number (Gr) : It is the relative strength of buoyant to viscous forces.
(iii) Prandtl Number (er) is the indicative of the idafive ability of the fluid to
diffuse momentum and internal energy by molecule
= Kinematic visocity
Thermal diffusity
(iv) Stanton number (St) is the ratio of 1 .. ni to the flow of heat per unit temperature rise due tothe velocity of the fluid
Q. 4.6. Prove the free convection correlation
Ans. Buckingham 3t method
7/28/2019 Convection Hmt
4/47
The functional relationship between variables affecting free convection can be
premised as;
There are 8 physical quantities (Bg and AT are counted separately) and 5fundamental units hence there are (85) = 3ir terms
Equating the exponents of fundamental dimensions on both sides
M :0a+1L: 0ab+c+d3
T: 0  a  b  2c
0: 0=bH: 0 = b
Equating the exponents of fundamental dimensions on both sides;
M: a1 0L: ab+c+d=0
T: abc=O (1: b 10
H: b+1=0
Solution of these equations give;
b = 1
a = 1c = 0
d= 0
7/28/2019 Convection Hmt
5/47
M: a + b = 0
L: a + b + c + d + 2= 0
T: a 3 h c  2 = 00: b1 = 0
Solving we get
b = 1
a = 1
c = 0d = 0
Solving we get
b= 1, a 0, c = 0, d = I
Thus the functional relation becomes:
Nu = (Re, Pr)Hence proved
7/28/2019 Convection Hmt
6/47
Q. 4.8. Define bulk temperature and mean film temperature.
Ans. Bulk temperature (tb) is defined as the arithmetic mean of the temperatures at inlet and exit
of heat exchanger tube.
Mathematically;
Mean film temperature (9 is the arithmetic mean of the surface temperature t5 of
a solid and the undisturbed temperature t of the fluid which flows past it.
Mathematically
Q. 4.9. Define local and average convective coefficient.
Ans. Consider the flow of fluid with velocity and temperature past astationary flat plate of length l and width
The local heat flux is given by;
Where is the local convective coefficient The total heat transfer rate Q is given by;
7/28/2019 Convection Hmt
7/47
Total heat transfer rate can also be expressed as;
where h = Average value of convective coefficient based on total surfa . Equating (i) and (ii)
Q. 4.10. Explain the formation of hydrodynamic boundary layer.
Ans. When a fluid flows around an object there exists a thin layer of fluid close to the solidsurface where velocity gradient exists. This thin layer of changing velocity has been called the
hydrodynamic boundary layer.
Consider the flow of fluid past a thin flat plate with sharp leading edge (fig. 4.4)
(I)For Re 5 x 1O the boundary layer is
turbulent. For 3 x
7/28/2019 Convection Hmt
8/47
(iii) The turbulent boundary layer does not extend to the solid surface underlying it is an
extremely thin layer called laminar sub layer.
(iv) For zone within the boundary layer, du / dy 0 while the condition for flow beyond theboundary layer and its outer edge are;
(v) The boundary layer thickness () is defined as the distance measured normal to the plate
surface at which u 0.99 u
(vi) For laminar boundary layer the velocity gradient becomes smaller along the flow directionand so does the shear stresses whereas for turbulent boundary layer the shear stresses at plate
surface have high value with steeper velocity gradient
Q. 4.11. What is a heat exchanger? What is its purpose? Give examples.
Ans. Heat exchanger is process equipment designed for effective transfer of heat energy between
two fluids, a hot fluid and the coolant. Noticeable examples are:
(i) Boi1ers(ii) Super heaters
(iii) Condensers
(iv) Automobile radiators(v) Evaporator of an ice plant
(vi) Water and air heaters or coolers.
The purpose of heat exchanger is to either remove heat from the fluid or to addheat to the fluid. The heat transferred may be in form of latent heat (Boilers and condensers) or
sensible heat (Heaters and coolers)
Q. 4.12. Classify different types of heat exchangers.
Ans. Heat exchangers can be classified according to:
(i) Operating principle(ii) Arrangement of flow path
(iii) Design and constructional detail
Classification of Heat Exchangers: Many types of heat exchangers have been developed tomeet the widely varying applications. Based upon their
. Operating principle
Arrangement of flow path Design and certain constructional features,
The heat exchangers can be classified into the following categories:
7/28/2019 Convection Hmt
9/47
Nature of heat exchange process Based upon the nature of heat exchange process, the heat
exchangers are classified into direct contact, generator arid respirators.
In direct contact or open heat exchangers, the energy transfer between the hot and cold
fluids is brought about by their complete physical mixing; there is simultaneous transfer
of heat and mass. Use of such units is restricted to the situations where mixing between the fluids is either
harmless or is desirable.
Examples are water cooling towers and jet condensers in steam power plants. Figure 4.5
represents a direct contact heat exchanger.
Steam is being bubbled into water; steam gets condensed and releases heat that warms up
the water.
In a regenerator, the hot fluid is passed through a certain medium called matrix. The heat
is transferred to the solid matrix and accumulates there; the operation is called heating
period.
The heat thus stored in the matrix is subsequently transferred to the cold fluid by
allowing it to pass over the heated matrix. The regenerators are quite often used in
connection with engines and gas turbines
.Other applications are:
Regenerators of open hearth and glass melting furnaces and air heaters of blast furnaces.
The operation of a regenerator is intermittent; the matrix alternately stores heat extracted
from the hot fluid and then delivers it to the cold fluid.
However in some of the regenerators the matrix is made to rotate through the fluidpassages arranged side by side and that renders the heat exchange process continuous.
The effectiveness of a regenerator depends upon the heat capacity of the regenerating
material and the rate of absorption and release of heat.
7/28/2019 Convection Hmt
10/47
In a recuperator, the fluids flow simultaneously on either side of a separating wall; the heat
transfer occurs between the fluid streams without mixing or physical contact with each other.The wall provides an element of thermal resistance between the fluids.
and the heat transfer consists of:
Convection between the hot fluid and the wall
Conduction through the wall Convection between wall and the cold fluid
Such exchangers are used when the two fluids cannot be allowed to mix, i.e., when
the mixing is undesirable. Majority of the industrial applications have exchangers of therecuperator type. Notable examples are:
(i) Boilers, superheaters and condensers ; economisers and the air preheaters in steam power
plants.(ii) Automobile radiators
(iii) Condensers and evaporators in refrigeration units.
(iv) Oil heaters for an airplane(v) Heat exchanger inside a gas furnace etc.
The opentype (direct contact) heat exchangers and recuperators operate under steady state
conditions ; and the transfer of heat inside a regenerator takes place essentially under transient
conditions.Relative direction of motion fluids: According to the direction of flow of fluids,
the heat exchangers are classified into three categories : parallel flow, counter flow and the cross
flow.In the cocurrent or parallel flow arrangement, the fluid (hot and cold) enter the unit from the
same side, flow in the same direction and subsequently leave from the same side (Fig. 4.7).
Obviously the flow of fluids is unidirectiamal and parallel b eh other.
In the countercurrent or counterflow arrangement0 the fluids (hot and cold) enr the unit from
opposite ends, travel in opposite directions and subsequently leave from opposite ends.
Obviously the flow of fluids is opposite in direction to each othet. For a given surface area, thecounterflow arrangement gives the maximum heat transfer rate and is naturally preferred for the
heating and cooling of fluids.
7/28/2019 Convection Hmt
11/47
In the crossflow arrangement, the two fluids (hot and cold) are directed at right angles to each
other. Figure 4.9 shows two common arrangements of crossflow heat exchangers. In figure 4.9
(a) the fluid A flows inside the separate tubes and its different streams do not mix. The fluid Bflows over the tube banks and gets perfectly mixed. In Figure 4.9(b), each of the fluid stays in
prescribed paths and are not allowed to mix as they flow through the heat exchanger. When
mixing occurs, the temperature variations are primarily in the flow direction. When unmixed,
there is temperature gradient along the steam as well as in the direction perpendicular to it.
Apparently, temperatures of the fluids leaving the unit are not uniform for the unmixed steams.The cross flow heat exchangers are commonly employed in air or gas heating and cooling
applications, e.g. the automobile radiator and the cooling unit of an airconditioning duct.
Mechanical design of heat exchange surface:
(i) Concentric tubes : Two concentric pipes are used, each carrying one of the fluids. The
direction of flow may correspond to unidirectional or counter flow arrangement.
(ii) Shell and tube : One of the fluids is carried through a bundle of tubes enclosed by a shell.
The other fluid is forced through the shell and flows over the outside surfaceof tubes. The direction of flow for either or both fluids may change during its passage
through the heat exchanger.
(iii). Multiple shell and tube passes : The two fluids may flow through the exchanger only once(single pass), one or both fluids may traverse the exchanger more than once (multipass). By
suitable header design, the fluid within the tubes (tube side fluid) can be made to traverse back
7/28/2019 Convection Hmt
12/47
and forth from one end of the shell to the other. Quite often longitudinal baffles are provided
within the shell which cause the fluid surrounding the tubes (shell side fluid) to travel the length
of shell a number of times. An exchanger having nshell passes and rntubes passes is designatedas nrn exchanger.
Q. 4.13. Define overall heat transfer coefficient.
Ans. Rate of heat transfer between two fluids is given by:
WhereA T = Temperature difference between two bodies.
R = Thermal resistance
Also,
whereU = overall heat transfer coefficient
A = surface area
From (1) and (ii)
When two fluids of heat exchanger are separated by plane wall (fig. 4.11) the thermal resistance
comprises
1. Convection resistance due to fluid film at inner surface,
7/28/2019 Convection Hmt
13/47
1. Wail conduction resistance, /KA
1. Convection resistance due to fluid film at outside surface,
A.=A0= AFor plane wail
Q. 4.14. What is fouling ? What are its effects?
Ans. Consider heat flux through a cylindrical wall separating two fluids (Fig. 4.12)
7/28/2019 Convection Hmt
14/47
The thermal resistance for clean and uncorroded surface is given by;
(Based on inner surface)
For small wall thickness
However during normal operation the tube gets covered by deposits of ash, soot, dirt and
scale etc. This phenomena of rust formation and deposition of fluid impurities is calledfouling.
Due to fouling the surface deposits increase thermal resistance with corresponding drop in
performance of heat exchange equipment. If h51 and h50 denote heat transfer coefficientsfor scale formation on inside and outside surface then thermal resistance due to scale
formation on inner and outer surface is;
7/28/2019 Convection Hmt
15/47
(Based on inner surface)
Fouling factors are determined experimentally by testing the heat exchanger inboth the clean and dirty conditions.
Q. 4.15. Sketch the variation in temperature during
(a) Condensation (b) Boiling
Ans
Q. 4.16. Draw the variation temperature in case of parallel and counter flow heat
exchanger. Also define logarithmic mean temperature difference.
Ans. Temperature variation of fluids for : (a) Parallel flow and (b) Counter flow is
shown below
7/28/2019 Convection Hmt
16/47
Logarithmic Mean temperature difference (LMTD) is given by;
Where
Parallel flow heat exchanger
Counter flow heat exchanger
= Inlet temperature of hot fluid= Outlet temperature of hot fluid
= Inlet temperature of cold fluid.
= Outlet temperature of cold fluid.
Q. 4.17. Derive the relation for logarithmic mean temperature difference (LMTD) for
parallel flow and counter flow heat exchanger.
Ans.
7/28/2019 Convection Hmt
17/47
(a) Parallel flow heat exchanger. Consider an elementary strip at the distance end of heat
exchanger. Let dx be the length of strip. Let at this section. the temperature of hot fluid be
th and that of cold fluid be t which are assumed to be constant
dQ = Heat flow through the elementary length dx.
Heat exchange between the fluids can be written as;
Heat capacity or water equivalent of hot fluid
Heat capacity or water equivalent of cold fluid.
(b) Counter flow heat exchanger
7/28/2019 Convection Hmt
18/47
In general
+ve sign refers to parallel flow heat exchanger and ye sign refers to counter flow heatexchanger.
Integrating (III) we get;
From equation (A) and (III)
Or
Integrating between inlet and outlet sections;
From (IV)
7/28/2019 Convection Hmt
19/47
Put this value in (VI) we get;
Q. 4.18. Define effectiveness and numb of transfer units and capacity ratio.
Ans. The effectiveness of heat exchanger is defined as ratio of energy actually
transferred to the maximum theoretical energy transfer.
Number of transfer units (NTU) : The number of transfer units (NTU) is a measure of thesize of heat exchanger, it provides some indication of the size of heat exchange_ It is
defined as;
Capacity ratio (C) : It is defined as ratio of minimum to maximum capacity rate.
Q. 4.19 Derive the relation for effectiveness of parallel flow heat exchanger.
7/28/2019 Convection Hmt
20/47
Ans. Consider the heat exchange through an incremental area dA as shown in fig.
From (I) and (II)
Integrating the above expression we get;
Solving
7/28/2019 Convection Hmt
21/47
Substituting this value in equation (III)
7/28/2019 Convection Hmt
22/47
Q. 4.20. Derive the relation for effectiveness of counter flow heat exchanger.
Ans. Consider the heat exchange through an incremental area dA of the exchanger
From (I)
Integrating the above equation between inset and outlet of heat exchanger
7/28/2019 Convection Hmt
23/47
From the definition of effectiveness;
Substituting these values in (II)
Let
7/28/2019 Convection Hmt
24/47
If c is assumed to be minimum i.e. c < Ch
Q. 4.21. Derive momentum equation for the hydrodynamic boundary layer.
Ans. For a twodimensional infinitesimal control volume (dx x dy x unit depth)within the boundary layer region, the viscous forces acting along with the momentum of
fluid entering and leaving the elementary volume have been indicated in fig. 4.18.
7/28/2019 Convection Hmt
25/47
Momentum change : The momentum flux in xdirection is the product of mass flowing in xdirection and the icomponent u of velocity. A fluid mass enters the left face at the rate p
udy producing an Imomentum influx
The momentum efflux through the right face is
Since we are concerned only with momentum in idirection, the momentum of the fluid
moving in ydirection is obtained by multiplying the mass moving in ydirection also withthe icomponent u of the velocity. Therefore the momentum influx from the bottom face is
mu = (p vdx) u
= p u v dx
and the momentum effux from the top face is
The resultant momentum change in xdirection is,
7/28/2019 Convection Hmt
26/47
= momentum efflux from the right and top faces  momentum influx from the left and
bottom faces
For the continuity equation (au/ax) + (av/ay) =0 and therefore the rt momentum
transfer in xdirection becomes:
Viscous forces : The shearing stress due to fluid viscosity is proportional to the
velocity gradient and is given by Newtons law c viscosity.
where u is the dynamic viscosity of the fluid
The shearing stress at the lower face of the control volume is r = u ( u/dy) aid the
corresponding shearing force for the area (dx x 1) is s (au/ay) dx. The shearing due to
viscosity at the upper face of the control volume is x + (r/.3ij) 4) and the correspondingshearing force for the area (dx x 1) is
Since the main stream flows in xdirection, the shearing force in ydirection can be
neglected. Therefore the net viscous force in the direction of motion is:
For a fixed control volume and steady flow, the Newtons second law of motion
stipulates that the resultant applied xforce equals the net rate of xmomentum transfer out of
the volume, i.e.,[(xmomentum efflux)  (xmomentum influx)]
7/28/2019 Convection Hmt
27/47
Neglecting the product of small quantities
Net energy convection
Likewise the net energy convection in the ydirection would be:
The conductive terms follow from the Fourier law, and the conduction heat rate in
the ydirection is
7/28/2019 Convection Hmt
28/47
Due to relative motion of fluid in the boundary layer (fluid on the top face of the
control volume moves faster than fluid on the boftom face), there will be viscous effectswhich will cause heat generation.
Viscous force = shear stress x area upon which it acts
This force will act through a distance s which can be determined by the relative
velocity of fluid flow at the upper and lower faces of element; s = (au/ ay) dy
With stipulations of steady state condition, the algebraic sum total of heat due to
convection, conduction and viscous effect equals zero. Thus
For a twodimensional boundary layer flow, (au/ax) + (av/oy) = 0, and therefore the aboveequation can be recast as
Which represents the differential energy equation for flow past a flat plate. If the heat
generation due to viscous effects is neglected, the energy equation takes the form
Q. 4.23. Draw the profile of thermal boundary layer during flow of cold fluid over a
warm plate.
Ans.
7/28/2019 Convection Hmt
29/47
If the approaching free steam temperature S above the plate surface temperature the
thermal boundary layer will have the shape depicted in fig. 4.20.
The temperature a the fluid changes from a minimum at the plate surface to the
temperature of the main stream at a certain distance from the surface.
At point A, the temperature of the fluid is the same as the surface temperature t. Tl
fluid temperature increases gradually until it acquires the free stream temperature t.
The distance AB, measured perpendicularly to the plate surface, denotes the
thickness of thermal boundary at a distance x from the leading edge of the plate.
The concept of thermal boundary layer is analogous to that of hydrodynamic boundary layer; the
parameters affecting their growth are however different. The velocity profile of the
hydrodynamic boundary layer is dependent primarily upon the viscosity of the fluid. In a thermalboundary layer the temperature profile depends upon the flow velocity, specific heat, viscosity
and thermal conductivity of the fluid The thermophysical properties of the fluid affect the
relative magnitude of 6 and
and the nondimensional Pradtl number (Pr = M ce/k) constitutes the governing parameter:
\
Q. 4.24 What is meant by dimensional homogeneity ? What is dimensionless number ?
How and where they are used in heat transfer?
7/28/2019 Convection Hmt
30/47
Ans. In heat transfer there are 5 fundamental quantities units i.e. mass (M), length (L), Time (T),
Heat (H) and temperature (0). For any equation to be dimensionally homogeneous the
dimensions of each term must be same. Hence principle of dimensional homogeneity states thatfor an equation to be dimensionally homogeneous the fundamental units of each term must be
same.
A dimensionless number is the ratio of different forces. For example:(1) Reynold Number = Inertia force
Viscous force
(ii) crash of Number = buoyant force x Inertia force(Viscous force)2
(iii) Nusselt Number = Temperature gradient at surface
Overall reference temperature gradient
(iv) Prandtl Number = Kinematic viscosityThermal diffusivity
free and forced convection correlations and hence heat transfer can be determined as
follows
Example 4.1. A nuclear reactor with its core constructed of parallel vertical plates 225 m
high and 15 wide has been designed on free convection heating of liquid bismuth.
Metallurgical considerations limit the maximum surface tempratur of the plate to 975C
and the lowest allowable temperature of bismuth is 325C Estimate the maximum possibleheat dissipation from both sides of each plate.
The appropriate correlation for the convection coefficient is
where the different parameters are evaluated as the mean film temperature.
Solution : At the mean film temperature t = (975 + 325)/2 = 650C, the thermo Length physical
properties of bismuth are:
7/28/2019 Convection Hmt
31/47
Using the given correlation
This gives a heat transfer of: Q = 2 hA At
The factor 2 accounts for two sides of the plate.
= 153 MW.
Example 4.1 A. A Hot plate 1x1.5m is maintained at 300C. Air at 25C blow
overs the plate. If the surface heat transfer coefficient is 20 W/m22C, Calculate the rate of
heat transfer.
Solution: We know that
Q = 20 x 1)C1.5(300  25)
= 20 x x 1.5 (275) 8250 W.
Example 4.2. Estimate the heat transfer from a 40 W incandescent bulb at 125C to
25C in quiescent air. Approximate the bulb as a 50 mm diameter sphere. What
percent of the power is lost by free convection?
The appropriate correlation for the convection coefficient is
when the different parameters are evaluated at the mean film
temperature, and the chrematistic length is the diameter of the sphere.
Solution: At the mean film temperature,
properties for air are:
7/28/2019 Convection Hmt
32/47
Using the given correlation,
This gives a heat transfer of
Therefore the percent of heat loss by free convection is
Example 4.3. A hot square plate 40 cm x 40 cm at 100C is exposed to atmospheric air
at 20C. Make calculations for the heat loss from both surfaces of the plate, if:(a) the plate is kept vertical (b) plate is kept horizontal. The following empirical
correlations have been suggested:
Nu = 0.125 (Gr Pr)33 for vertical position of plate, and
Nu = 0.72 (Gr Pr) for upper surface
0.35 = (Gr Pr) for lower surface
where the air properties are evaluated at the mean temperature.
Solution: At the mean temperature, t (100 + 20)/2 = 60C
the thermo physical properties of air are
= 0.724
1. When the plate is oriented vertically,
This gives a heat transfer of : Q = 2h AAtThe factor 2 accounts for two sides of the plate
7/28/2019 Convection Hmt
33/47
Q = 2 x 5.508 x (0.4 x 0.4) x (10020) = 141 W
(b) When the plate is positioned horizontally
(1) For upper surface:
(ii) For lower surface
Comments : The above calculations show that the plate loses more heat when it is
oriented vertically. Obviously natural cooling can be achieved more effectively by keeping the
plate in vertical position
Example 4.4. The lubricating oil for a large industrial gasturbine engine is cooled in a
counter flow, concentric tube heat exchanger. The cooling water flows through the inner
tube (d = 25 mm) with inlet temperature 25C and mass flow rate 0.2 kg/s. The oil flows
through the annulus (d0 =50 mm) with mass flow rate 0.125 kg! s and its temperature at
entry and exit are 90C and 60C respectively. Neglecting tube wall thermal resistance,
fouling factors and heat loss to surroundings, make calculations for outlet temperature of
cooling water, overall heat transfer coefficient and length of the tube.
The relevant thermophysical properties of engine oil and water are as given below:
Solution : For the flow arrangement and temperature distribution of hot fluid
(engine oil) and cold fluid (water) in a counter flow, concentric tube heat exchanger.1. From energy balance,
The subscripts Ii and c refer tu hot (oil) and cold (water) fluids respectively.
Output temperature of cooling water,
(b) Reynolds number for flow of water through the tube is
7/28/2019 Convection Hmt
34/47
Since Re> 2300, the flow is turbulent and accordingly the following correlationapplies for calculating the heat transfer coefficient on the inside (water side),
The oil flows through the annulus with hydraulic diameter,
Since Re
7/28/2019 Convection Hmt
35/47
Neglecting fouling effects and thermal resistance of the tube material, the overallheat transfer coefficient is
1. The logarithmic mean temperature difference for counter flow arrangement
The heating surface area also equal (2r 41) where d and 1 represent the pipe diamer
and length respectively.
Example 4.5. A chemical industry operates continuously and produces 2 kg of sulphuric
acid per day which needs to be cooled from 60C to 40C in a counter flow double pipe heat
exchanger. The acid flows through the inner pipe while water employed as cooling medium
flows through the annulus with temperature 15C at entry and 20C at exit. The inner
diameters for the inner and outer pipe are 70 mm and 120 mm respectively, and each pipe
is 5 mm thick. Presuming that thermal conductivity of inner pipe material is 48 W/m K,
make calculations for the mass flow rate of water and length of the heat exchanger.
The thermophysical properties of water and sulphuric acid at the mean bulk temperature
are given below:
Property Water
Acid
Density (kg/rn3)
998
1800
7/28/2019 Convection Hmt
36/47
Sp. heat (J/kg )
Thermalconductivity
(W/mK)
Kinematic viscosity (m2/s)
Fouling factor (m2 1(/W)
4187
0.60
1.0 x 106

1465
0.30
6.8 x 10.6
0.0002
Solution : (a) The mass flow rate of water can be determined from an energy balance on the twofluids. That is heat gained by water = heat lost by acid
(h) For counter flow arrangement
For the given configuration, the ove7all heat transfer coefficient is prescribed bythe relation
The heat transfer coefficients h1 for inner side (for acid side) and h0 for outer sideof pipe (for water side) are worked out as follows
For inner side of pipe:
Since Re > 2300, the flow is turbulent and the following correlation applies forCooling
7/28/2019 Convection Hmt
37/47
For outer side of pipe:Hydraulic diameter of annulus,
Since Re> 2300, the flow is turbulent and accordingly Dittus Boeltier correlation
for heating applies
Substituting the relevant values in expression (i), we get
The length of the heat exchanger can then be calculated as
67824 = 130.04 x (j x 0.08 x 1) x 31.91 ; 1 = 65.07 m
Comments : The heat exchanger has a long length. It would be appropriate
replace the double pipe heat exchanger by a shell and tube type heat exchanger.
Example 4.6. A counter flow heat exchanger is used to cool 2000 kg/hr of oil (c = 2.5 kJfkg
K) from 105C to 30C by the use of water entering at 15C. If the overall heat transfer
coefficient is expected to be 1.5 kW/m2 K, make calculations for the water flow rate, the
surface area required and the effectiveness of heat exchanger. Presume that the exit
temperature of the water is not to exceed 80C. Use NTUeffectiveness approach.
Solution (a) The mass flow rate of water can be determined from an energy balance on the two
fluids, i.e., heat lost by oil (hot fluid) = heat gained by water (coolant)
7/28/2019 Convection Hmt
38/47
1. Thermal capacity of the water stream (coolant)
Thermal capacity of the oil steam (hot fluid)
When hot fluid has the minimum heat capacity, then
The number of transfer units (NTU) can be computed from the following expression for
effectiveness of a counter flow exchanger
Rearranging
Therefore the heat transfer area is
Example 4.7. A counterflow exchanger of surface area 8 m2 is to be used to heat a process
liquid by using a high temperature water available from another part of the plant. If the
overall coefficient of heat transfer is 450 W/m2 K, find the exit temperatures of the process
liquid and water stream from the data given below:
7/28/2019 Convection Hmt
39/47
Solution : Thermal capacity rate of the lt (water stream) and cooling (process liquid) fluid
are:
The effectiveness for a counter flow heat exchanger is,
Alternatively using the parameters C = 0.667 and NTU = 0.857, we get E = 0.495.The hot fluid has the minimum thermal capacity and therefore in terms of
temperature differences
Outlet temperature of the hot fluid (water),th2 = 3650.495 (365300) = 332.82 K
From energy balance on the two fluids,
Outlet temperature of the cold fluid (process liquid),
Example 4.8. The engine oil at 150C is cooled at 80C in a parallel flow heat exchanger by
water entering at 25C and leaving at 60C. Estimate the exchanger effectiveness and the
number of transfer units. If the fluid flow rates and the inlet conditions remain unchanged,
work out the lowest temperature to which the oil may be cooled by increasing length of the
exchanger.
Solution: (a) From energy balance on the hot (oil) and cold (water) fluids,
7/28/2019 Convection Hmt
40/47
Apparently, the hot fluid has the minimum thermal capacity and
In terms of capacity ratio and number of transfer units,
exp [1.5 NTUI = 11.5 0.56 = 0.16
Number of transfer units, NTU 1.221.
1. The exit temperature of oil would be minimum corresponding to the situation when the
exchanger is increased infinitely or NTU 
Therefore, the minimum possible exit temperature of the oil is
= 150  0.667 (150  25) = 66.62C
Example 4.9. A parallel flow heat exchanger uses 1500 kg/hr of cold water entering at 25C
to cool 600 kg/hr of hot water entering at 70C. The exit temperature on the hot side is
required to be 50C. Neglecting the effects of fouling, make calculations for the area of heat
exchanger. It may be presumed that the individual heat transfer coefficients on both sides
are 1600 W/ni2 K. Use the mean temperature difference approach and the effectiveness
NT1J approach.
Proceed to calculate the exit temperature of the cold and hot streams if the flow of hot
water is doubled, i.e., it becomes 1200 kg/hr. It has been stated than the individual heat
transfer coefficients are proportional to 0.8th power of flow rate. For water C 4180 J/kg K.
Solution : The unknown exit temperature of the cooling water can be found from an energy
balance on the two fluids. That is
7/28/2019 Convection Hmt
41/47
From energy balance on the hot fluid, the heat transfer rate is
Mean temperature difference approach:
Effectiveness  NTU approach:Thermal capacity rates of the hot and cold fluids are:
Obviously
Capacity ratio, C
Effectiveness, E
The effectiveness for a parallel flow heat exchanger is given by
7/28/2019 Convection Hmt
42/47
Upon solution we obtain: NTU = 0.695
Heating surface area, A = 0.695 x 696.67800
= 0.605 m2
The second part of the problem can be worked out more easily by using thefectiveness  NTU approach.
Since the flow rate is doubled on the hot side,
Capacity ratio C = 1395.33/1741.67 = 0.801Transfer units NTU
Invoking the effectiveness relation for parallel flow heat exchanger,
Upon solution we get;
= 70 0.305 x 45 = 56.27C
From energy balance,
7/28/2019 Convection Hmt
43/47
Example 4.10. Oil with a mean specific heat of 2.5 kJ/kg. K is to be cooled from 110C to
30C in a single pass counter flow heat exchanger. The coolant is water which enters at
20C and leaves at 80 C and the overall heat ttansfer coefficient for this type of heat
exchanger is 1.5 kW/m2 K. If the water flow rate is 1500 kg/hr, determine the quantity of
oil that can be cooled per hour and the heat exchanger area. (b) What would be the fluid
exit temperatures when the water flow rate is decreased to 1000 kg/hr for the same oil flow
rate ? Comment upon the results.
The effectiveness of a counter flow heat exchanger is given by the following
expression where NTU is the number of transfer units and C is the capacity rate ratio
Solution: (a) The mass flow rate of oil can be determined from an energy balance on the two
fluids, i.e.,
Heat lost by oil (hot fluid) = heat gained by water (coolant)
mh x 2.5 (110  30) = 1500 x 4.186 (80  20) = 376740 kJ/hr
Therefore the oil flow rate is,
= 3767402.5x80
= 1884 kg/hr
Thermal capacity rate of the hot (oil) and cold (water) fluid are
Capacity ratio, C
When the hot fluid (oil) has the minimum thermal capacity, thenEffectiveness,
Rearrangement of the given expression gives:
7/28/2019 Convection Hmt
44/47
:. Heat transfer area, A
Note : The heat exchange area can be found more conveniently by the LMTD
approach.For the counter flow arrangement, the end temperature difference are:
Now, the heat exchange, Q = UAO,,,
(h) The changed thermal capacity rates of the hot (oil) and cold (water) fluid are:Ci =1884 x2.5=4710kJ/hrK
Cc =1000x4.186=4186kJ/hrK
Inserting the appropriate values in expression (i),
When the coolant (water) has the minimum thermal capacity, then
7/28/2019 Convection Hmt
45/47
Outlet temperature of the coolant (water)
t2 = 0.868 (110 20) + s 20
= 98.12C.
Example 4.11. In a center flow heat exchanger, oil (c=3kJ/kg k) at rate of 1400 kg/ hr is
cooled from 100C to 30C by water that enters the exchanger at 20C at rate
1300 kg/hr. Determine heat exchanger area from an overall heat transfer coefficient 3975
kJ/m2 K. Also derive the relationship between oil and water temperature at any section of
heat exchanger.
Solution.
(ii) At any section of heat exchanger
7/28/2019 Convection Hmt
46/47
Q. 4.12. A heat exchanger is to be designed to condense an organic vapour at a rate of 500
kg/mm which is available at its saturation temperature 355 K. Cooling water at 286 K is
available at a flow rate of 60 kg/s. The overall heat transfer coefficient is 475 W/m2C.
Latent heat of condensation of the organic vapour is 600 kJ/kg. Calculate:
(i) The number of tubes required, if 25 mm o diameter, 2 mm thick and 4.87 m long tubes
are available, and
(ii) The number of tube passes, if the cooling water velocity (tube side) shouldnot exceed 2 iVs. (M.U.)
Ans. Given
d0 = 25 mm = 0.025 m; d. = 25 2 x 2 = 21 mm = 0.021 m ; L = 4.87 m;
(I) The number of tubes required, N:
Heat lost by vapour = heat gained by water
Logarithmic mean temperature difference (LMTD) is given by
Heat transfer rate is given by,
N = 470 tubes Ans.
(ii) The number of tube passes, p:
The cold water flow mass passing through each pass (assume p are number of
passes) is given by,
7/28/2019 Convection Hmt
47/47
= 4.91 = 5 Ans.